Article no.: 80087075
kostenlose Anfrage / free request
from 1 € 0.00 € 0.00
The EnOcean Gateway is used to connect EnOcean sensors/actuators (max. 30 EnOcean S/A), such as pushbuttons, remote controls, temperature sensors, etc. to the ISYGLT BUS technology. The Gateway can manage up to 8 virtual sensor/actuator modules. In turn, up to 4 sensors/actuators can be operated on each virtual sensor/actuator module. The EnOcean-ISYGLT-01 and EnOcean-DALI-01 sensor/actuator modules can also be integrated.
|Supply voltage||9-24V DC|
|Connection||RJ10 plug, RS-485-BUS|
|Assembly||screwing, gluing, inserting|
|Scope of delivery||20cm cable, RJ10 distributor|
|Operating temperature||-20°C to +65°C|
|Storage temperature||-20°C to +70°C|
|Humidity||0-85% r.h. non-condensing|
|Design||Mini PVC housing|
|Dimensions||LxWxD 79.5 x 25.5 x 16mm|
|Weight||37g (incl. cable and connection adapter)|
The module has no DIP switches.
The address is set via the virtual addressing module "ISYGLT-ADR" in the ProgramDesigner.
|Flashes slowly||The module is ready for operation in delivery state without BUS address.|
|Flashes quickly||The module is ready for programming and addressing.|
|OFF||The module has been successfully programmed and uses 1-8 BUS addresses (check via simulator (debugger) in ProgramDesigner).|
|Programming button||Operating mode|
|Push > 3s||The module changes to the address programming mode (LED flashes quickly). Now the addressing can be done with the ProgramDesigner.|
|Briefly push||Exiting the address programming mode|
|Push > 8s||Reset - the module is returned to the delivery state without address(es).|
Coupling to EnOcean components is carried out in the ProgramDesigner. Information on this and on the virtual sensor/actuator modules can be found in the current ProgramDesigner version in the "EnOcean" module group.
These virtual modules get a BUS address. The EnOcean components are configured in the parameters of the virtual modules. The virtual sensor/actuator modules are also automatically assigned to the gateway by the BUS address assignment of the gateway module.
Each ISYGLT GW-EnOcean-08 can manage up to 8 sensor/actuator modules.