Article no.: 80087075
kostenlose Anfrage / free request
from 1 € 0.00 € 0.00
The EnOcean Gateway is used to connect EnOcean sensors/actuators (max. 30 EnOcean S/A), such as pushbuttons, remote controls, temperature sensors, etc. to the ISYGLT BUS technology. The Gateway can manage up to 8 virtual sensor/actuator modules. In turn, up to 4 sensors/actuators can be operated on each virtual sensor/actuator module. The EnOcean-ISYGLT-01 and EnOcean-DALI-01 sensor/actuator modules can also be integrated.
|RJ10 plug, RS-485-BUS
|screwing, gluing, inserting
|Scope of delivery
|20cm cable, RJ10 distributor
|-20°C to +65°C
|-20°C to +70°C
|0-85% r.h. non-condensing
|Mini PVC housing
|LxWxD 79.5 x 25.5 x 16mm
|37g (incl. cable and connection adapter)
The module has no DIP switches.
The address is set via the virtual addressing module "ISYGLT-ADR" in the ProgramDesigner.
|The module is ready for operation in delivery state without BUS address.
|The module is ready for programming and addressing.
|The module has been successfully programmed and uses 1-8 BUS addresses (check via simulator (debugger) in ProgramDesigner).
|Push > 3s
|The module changes to the address programming mode (LED flashes quickly). Now the addressing can be done with the ProgramDesigner.
|Exiting the address programming mode
|Push > 8s
|Reset - the module is returned to the delivery state without address(es).
Coupling to EnOcean components is carried out in the ProgramDesigner. Information on this and on the virtual sensor/actuator modules can be found in the current ProgramDesigner version in the "EnOcean" module group.
These virtual modules get a BUS address. The EnOcean components are configured in the parameters of the virtual modules. The virtual sensor/actuator modules are also automatically assigned to the gateway by the BUS address assignment of the gateway module.
Each ISYGLT GW-EnOcean-08 can manage up to 8 sensor/actuator modules.