Article no.: 80087077
kostenlose Anfrage / free request
from 1 € 0.00 € 0.00
The EnOcean DALI-01 Actuator Module is used for wireless radio connection of lights with DALI ballasts. A wide range of DALI control modes is possible via software parameterisation.
These are for example:
Each ISYGLT Gateway GW-EnOcean-08 can manage and control up to 8 virtual "A EnOcean ISYGLT DALI" Actuator Modules. Up to 4 EnOcean-DALI-01 Modules can be linked to each virtual "A EnOcean ISYGLT DALI" Actuator Module via radio ID and controlled in synchronisation.
|DALI power supply, D4i, OSRAM DEXAL ECG
|2-pole spring-loaded terminal
|screwing, gluing, inserting
|Scope of delivery
|20cm cable, RJ10 distributor
|-20°C to +65°C
|-20°C to +70°C
|0-85% r.h. non-condensing
The EnOcean-DALI-01 Actuator Module is connected for operation with an ISYGLT GW-EnOcean-08 Gateway. For the connection, the module must be in delivery state (LED flashes slowly). The EnOcean radio ID (8-digit hex number) is also required. This can be found on the module label.
|The module is ready for operation in delivery state without BUS address.
|The module is ready for programming and addressing.
|The module has been successfully programmed and uses 1-8 BUS addresses (check via simulator (debugger) in ProgramDesigner).
|If "Blitz bei Empfang" (means "Flash on reception") has been activated in the module parameters, the LED indicates the reception activity.
|Push > 3s
|The module changes to the address programming mode (LED flashes quickly). Now the addressing can be done with the ProgramDesigner.
|The module sends its EnOcean radio ID. So the ID can be displayed e.g. with the DolphinView programme.
|Push > 8s
|Reset - the module is returned to the delivery state without address(es).
The module is set up in ProgramDesigner according to its use.
The used BUS address must exist in ISYGLT GW-EnOcean-08. Afterwards the parameters must be transferred. Shortly afterwards the connection with the Gateway is registered and available.
If the module should be connected to another Gateway, it must be reset to delivery state by a long button press (> 8s).
Article no.: 80087077